For clarification on a specific clause
within an Australian Standard,
contact the ESV Gas Safety Technical
Information Line on 1800 652 563.
Rating Cause Clause description
8 AS/NZS 5601.1 2013 DESIGN OF CONSUMER PIPING – Building isolation
Clause 5.2.10 5 Non-compliances
Breaches » Consumer piping does not have a manual shut-off valve at the each point of entry of piping to each building.
» The manual shut-off valve is not accessible and external to the building.
» A durable permanent sign has not been located in a prominent position adjacent to the valve.
The sign shall include the wording ‘GAS VALVE’.
9 AS/NZS 5601.1 2013 REQUIREMENTS FOR GAS APPLIANCES – Australian requirements
Clause 6.1.2 5 Non-compliances
Breaches Appliances do not comply to specifications, Standards of performance and certification requirements.
10 AS/NZS 5601.1 2013
ADDITIONAL REQUIREMENTS FOR INSTALLATION OF SPECIFIC GAS
APPLIANCES – Laundry dryers – Exhaust duct requirements
No provision for lint removal, access to be provided.